The Fireguard FT range is a compact tubular driven fire shutter that
provides a fire protection barrier for 1 – 4 hours.
The Fireguard FT range is a fire roller shutter that can be specified as:
• 1 hour fire protection. FT01
• 2 hour fire protection. FT02
• 4 hour fire protection. FT04
The Fireguard FT Compact range is manufactured to BS EN 1634-1 & BS 476 Part 22 standard.
Constructed from steel sections of 76mm cold rolled 20 gauge galvanised steel. The FT60 shutter provides a
defence against the spread of fire and can be used as a security door on a day to day basis.
The compact design allows the FT compact range to be installed in areas where traditional fire shutters are not
The system can we linked to audio / visual deacon fire alarms to ensure automatic closing in case of fire detection
with battery backup in the event of power failure.
Tested Report Number WF314225 - BS 476 Part 22 & BS EN 1634-1:2008
The Fireguard FT roller shutter is commonly used in kitchen servery areas, schools, hospitals and commercial offices where installation restrictions for space require a compact system.
76mm flat galvanised steel lath
12.5kg per square metre (dependant on size)
Galvanised bright rolled mild steel. Polyester powder coat colours are available at additional cost.
1.5mm bright spangle galvanised pressed steel coil casing available in various different designs to suit individual circumstances.
Overall height (top of box)
Up to 2000mm Box Size 250mm
Up to 3000mm Box size 300mm
Up to 4000mm box size 350mm
On larger widths the box sizes may move up one size due to deflection.
Galvanised steel standard, polyester powder coat colours are available.
50mm x 32mm x 3mm - 76mm x 32mm x 3mm
Dependant on width and height.
Galvanised steel standard polyester powder coat colours are available.
A tubular motor within the barrel assembly with limit switches and thermal cut out to prevent overheating. Draw 240 volts and 0.5 - 2.5 amps dependant upon the shutter size.
Complete with battery back up system that will enable self closure in the event of power failure.
Provision of a 13 amp fused spur is required for installation.
Fire panel that can be interconnected to the fire alarm to allow closing when receiving fire signal. Audio visual warning and timer delay.
Important note: Maintenance of fire shutters is required under the Regulatory Reform (Fire Safety) Order 2005 for companies. Failure to do so may invalidate insurance cover and building fire certification under the control of the local fire officer.
It is essential that the structural surround to the opening has a fire rating of at least the equivalent to the fireguard product specified and is sufficient for fixings to ensure fully compliant installation.
HAG operates a policy of continuous improvement. Product specification may change and it is advisable to consult with HAG technical advisors before specifying or ordering.